Payment & Shipping Terms:
|FP-51 KM:||Air Volume (m3/h )510||FP-68 KM:||Air Volume (m3/h )680|
|FP-85 KM:||Air Volume (m3/h )850|
fan coil units,
horizontal fan coil unit
FP-51KM FP-68KM FP-85KM FP-102KM FP-136KM FP-170KM FP-204KM FP-238KM
Fan coil is widely used in central air conditioning system equipment, at the end of the specification is the full name of the central air-conditioning fan coil units, can be simple classification is as follows:
Central air-conditioning fan coil units shall, in accordance with the form is divided into: horizontal dark outfit, horizontal load and vertical dark, vertical installed Ming, cassette five;
Cassette fan coil units shall, in accordance with the presence of condensate pump can be divided into: the ordinary type, luxury;
Horizontal fan coil according to thickness can be divided into: ultra-thin, ordinary;
Central air-conditioning fan coil unit according to the size of the static pressure can be divided into: 0 pa, pa 12, 30 pa, pa, pa 80, 50 is closed to static pressure;
Central air-conditioning fan coil number according to the exhaust pipe can be divided into: two rows of tubes, three rows of tubes;
And the two control and four control points: two controls common cold water cooling, fan coil summer winter go hot water heating;More than four control fan coil is used for a few more luxurious place, can go hot and cold water at the same time, can according to need some refrigerating room, some room to keep warm.
The selection of fan coil units to note: fan coil sample abroad, tend to give different closed under the static pressure of airflow and cooling capacity, to facilitate users to choose.Although some foreign concise sample only giving the name of air volume, but its meaning is different from the standard in our country, it generally refers to the air under a certain closed static pressure value, so the name of the air volume of similar foreign fan coil units, air volume will be 20% ~ 50% higher than domestic units.
Is also need to emphasize that using concise sample abroad, must pay attention to foreign companies tend to implement different standards and the meanings of the nominal volume also exist some differences.So choose, it is best according to the latest sample data is complete, or ask for delivery
Manufacturers to provide product under different closed static pressure of cold air volume and value, to determine the reliability.
Developed a variety of types of fan coil units: choose the fan coil units, in addition to the cooling quantity meet the requirement of the calculation of cooling load, also for the quantity of sensible heat and latent heat of match to meet the requirements of the hot wet room than;Must satisfy the supply air temperature difference air volume, ventilation rate and air distribution, etc.Along with the expanding the application range of the fan coil units, the difference in the types of air conditioning room service also will be more and more big.Requirements of the use of different properties and different air conditioning room, hot wet ratio is not the same, the amount of cold air volume matching should not be the same.Even if the same room air conditioning requirements and net volume, because of weather conditions, toward or differences, such as palisade structure can also lead to the different cooling load, clearly must be made with different structural characteristics of fan coil units, to meet the different needs of the room.And currently used in fan coil units, most is three rows of tubes, each row of eight root canal of the same kind of form, is clearly not meet the requirements of different rooms.Even if required cooling load, may also lead to low load room room temperature gradient caused by insufficient air volume and air changes and volatility is too large, reduce air conditioning accuracy and comfort;If you use the same air volume of the unit, and may cause high room cannot be guaranteed due to lack of cooling load temperature and humidity requirements.So different using conditions and requirements of air conditioning room, should choose different types of fan coil units, respectively.
Some experts advocate developing two rows of fan coil units, that can reduce the supply air temperature difference and increase the air changes, help to improve precision of the air conditioning and comfort.Under the same amount of cooling, the use of small temperature difference, big air volume air supply, will be better than, large temperature difference air supply air conditioning effect;Coil with a variety of waterway design.At present, the production of three rows of pipe coil, regardless of the length, all use the same SanJin for three out of the water.In order to reduce water resistance, increase cooling capacity, different water should be used in different length of coil design.As the carrier of 2 x 8 coil, respectively used two into two out, SanJin three out of four and out three different and waterways.These ideas its essence is to meet different processing requirements of the room, the specific choice depends on applications.
Principle of fan coil units 1, fan coil system working principle: fan, fan coil is mainly composed of heat exchange coil tube and casing, according to the fan static pressure outside the pipe can be divided into standard and high static pressure type, according to the heat exchange coil tube row number can be divided into two rows and three rows, so the heat exchange coil is usually adopts copper pipe string of aluminum fin, copper pipe diameter for 10 to 16 mm, fin thickness is about 0.15 ~ 0.15 mm, spacing of 2.0 ~ 3.0 mm, generally adopts double fan into the wind before curved blade centrifugal fan, motor USES capacitive 4 single phase motor, three gear speed, casing and water plate heat coagulation.
requirements of temperature and relative humidity.Used in cold water or hot water coil, the cold source and heat source supply.At the same time, by focusing on fresh air after fresh air conditioning room, through specialized fresh air pipe separately for each air conditioning room, to meet the requirement of air conditioning room.
Fan coil air conditioning system is compared with the centralized system, there is no big wind, only the pipe and the smaller air tube, has the arrangement and easy installation, being a small architectural space, separate good adjustment, which is widely used for temperature, humidity, accuracy is not high, room number, room smaller, requires a separate control of comfort air conditioning.
Working principle of the fan coil control fan coil control with local control scheme, divide into two kinds: simple control and temperature control fan coil simple control: use three-speed switch directly manually three-speed switch and start-stop control fan.Fan coil temperature control: using temperature controller according to the set temperature and actual testing temperature compare, operation, automatic control electric two/three way valve open and close;Three fan speed conversion.Or directly control the fan three-speed switch and start-stop, thus by water or air volume control system to achieve the purpose of constant temperature.
Fan coil structure of fan coil air conditioning system is composed of fan and coil unit directly in the room, when the work coil according to need to flow of hot or cold water, fan sucked into the unit, the indoor air is filtered after coil cooling or heating again after back to indoor, so in order to achieve the purpose of adjusting indoor temperature and humidity.
1 overview, fan coil units, fan coil is widely used in central air conditioning system of air processing equipment, is characterized by compact structure, flexible use, easy installation, low noise, low price, is a kind of applicable to different function building comfort air conditioning universal equipment, due to the performance of the fan coil is according to the design and calibration of standard, when used in conditions of use a different room, in the selection of fan coil units should be reduced and fixed.
2, fan coil fan, fan coil structure is mainly composed of heat exchange coil tube and casing, according to the fan static pressure outside the pipe can be divided into standard and high static pressure type, according to the heat exchange coil tube row number can be divided into two rows and three rows, so the heat exchange coil is usually adopts copper pipe string of aluminum fin, copper pipe diameter for 10 to 16 mm, fin thickness is about 0.15 ~ 0.15 mm, spacing of 2.0 ~ 3.0 mm, with double inlet air fan before curved blade centrifugal fan, motor USES capacitive 4 single-phase, three gear speed, chassis and condensate plate heat insulation.
Fan coil installation design points
1, fan coil installation of condensed water outlet pipe should be set up to the nearest tube drainage, which can shorten the distance of horizontal drainage, reduce the water by the drain slope is not enough, and risk of dripping.Lead to drain from the each fan coil diameter with phi 20 advisable, and the size of the drainage riser and manager also thrown.
2, in the fan coil units with hot and cold water pipes installed over the manual and electric water valve should be set below the water dish.The water dish plate connected with fan coil set water, also can ask the manufacturer to the original water pan is longer, to ensure that the valve such as the joint can condensate water pan is along the discharge.Insulation and should be closed to prevent secondary condensate.
3, fan coil installation should have access, its location and size, concrete engineering with construction closely, talk things over solve.Install fan coil units should be paid attention to in the small condole top tear open outfit is convenient, because it is necessary for the fan coil usage and maintenance.
4, fan coil installation inlet filter, to be loaded in order to protect the plate clean, otherwise the heat exchange efficiency low soon
5, pay attention to when will pick up on fan coil air duct, should choose high static pressure fan coil equipment.
6, to indicate the installation position of water valve in order to avoid reverse.Now a lot of engineering water valve upside to remind don't put the "0" when the power supply wiring line is wrong, wrong is going to burn out fan coil motor.
|model||FP-51 KM||FP-68 KM||FP-85 KM||FP-102 KM||FP-136 KM||FP-170 KM||FP-204 KM||FP-238 KM|
|Air volume (m3/h )||high-grade||510||680||850||1020||1360||1700||2040||2380|
|noise dB(A )||high-grade||39||40||42||44||45||48||50||51|
|Pressure of work(MPa)||1.6|
|Coil form||Copper tube and aluminum heat sink mechanical expanding|
|The motor||form of||Single-phase asynchronous motor|
|fan type||Low noise centrifugal fan|
|In and out of the water pipe||R c3/4"(internal thread)|
|Condensed water pipe||DN20|
|Line shape (length x width x height)(mm)||570×570×255||835×835×240||835×835×280|
|unit weight kg||20||20||23||24||25||27||28||28|
|Hoisting installation size (L*W)(mm)||600×400||780×680|
The unit performance parameter list:
Cardiac cooling conditions: into the dry bulb temperature of 27 ℃, WenQiu temperature 19.5 ℃, the water temperature 7 ℃, the water temperature of 12 ℃;
Cardiac heating conditions: into the dry bulb temperature of 21 ℃, water temperature 60 ℃;
His table water flow, water resistance and noise is refers to the parameter under the high speed air flow.
Cardiac due to improve product performance, the above parameters is likely to change.Changes due to improve product performance and our company keep product design will not be the right to advance notice, please refer to our nameplate parameters.